Anyone who owns an oil furnace understands how vital the pilot light is for your home.
- It is the a single component that certifies if your oil furnace is still in nice working condition, especially after a long period of being unused.
It is therefore not surprising whenever a single panics if it refuses to light, however, this should not be an issue that regularly makes you restless unless you attempt to relight it a few times to no avail. Fortunately, I can tell you that the pilot relighting process is simple. All you need to do is first switch off the internal gas valve for at least numerous minutes. This will allow the escaped gas to therefore dissipate slowly… You can then proceed to hold and press the valve while turning the pilot. Then, carefully using a BBQ lighter, relight the pilot light. Do not let go of the pressed valve for a few minutes to ensure that the pilot light lights up and remains lit. You may have to repeat this step a few more times before it finally agrees to light. However, if it is adamant after some relighting attempts, then you need to replace the panel cover. You may need to know what could cause this failure to relight. Occasionally the solution lies in first complication shooting and understanding the whole problem. One of the correct problems is the gas supply. If it has been somehow interfered with, then the chances are that the pilot light will not light. A badly cracked heat exchanger may also be another trigger that needs professional intervention to resolve. In case you are stuck, do not fear turning to your Heating and Air Conditioning expert in winter.